4.4.2. Any standpipe and hose system shall be:
(a) so calculated as to meet the flow and pressure requirements of the Fire Department;
(b) provided with connections for the Fire Department, located on the street side and clearly indicated so as to permit easy and fast attachment;
(c) distributed in hose stations which are:
i. easily accessible;
ii. located so that any part of the building is within 6 m from the nozzle when the hose is extended;
iii. installed in a hose cabinet containing the hose and its rack, the necessary connections from the 4th storey, a hose valve, and an approved extinguisher. The hose shall be connected and ready for use at any time;
(d) inspected at least annually.