8.143. A contractor or owner-builder may not install a pump island, unless it has, for each dispenser, a dispenser sump that meets the requirements of CAN/ULC-S664, Standard for Containment Sumps, Sump Fittings, and Accessories for Flammable and Combustible Liquids, or CAN/ULC-S653, Standard for Aboveground Horizontal Steel Contained Tank Assemblies for Flammable and Combustible Liquids, published by Underwriters’ Laboratories of Canada; that requirement does not apply to a pump island on a floating wharf.
O.C. 220-2007, s. 1; O.C. 87-2018, s. 511.